October 13, 2005 at 10:32 am · Thomas · Comments Off on Chimney Maintenance and Updates
The Chimney was one of the items the initial inspection uncovered as needed correction.
Upon inspection the flue pipe inside of chimney had been damaged with the exception of the top 6-8 feet and at base of chimney. Brick and mortar were seen in the space where the flue pipe had been damaged. The chimney needed to be brought up to code in order for the buildings gas to be restored.
Because the chimney did not meet code requirements, the owners contracted U.S. Chimney Corp of East Meadow NY to perform the following work:
- Brick/mortar and debris removal
- Installation of a lining system